[ENG] 10.6. [DKSF 48.5 IU] Reset Signal and Initial Output States
At the start of the logic, it is possible to set the outputs and the equipment they control in a known and predetermined initial state. To do this, use the rules with the entry "Initial Reset".
The rule "Initial reset" with the condition "Enables" is triggered 5 seconds after the reset. The rule with the term “Ended” is triggered in 10 seconds after the reset. After that, the usual application of the rules starts with sources other than “Initial reset” in an infinite loop. So, it is possible to generate a 5-second external reset pulse at one or more outputs or to ensure the correct sequence of power supply to external devices.